Will Depart in...
Started by Ed, September 02, 2020, 06:37:29 AM
0 Members and 1 Guest are viewing this topic.
Quote from: Trevor Hale on September 02, 2020, 12:57:38 PMHey Ed.I am not an electrician. But I do know / Understand Electrical in Ontario.I would NOT do the double pole breaker. The Double Pole Breaker will give you opposing phases (thus 240V) this would not be approved by the building code. What I would do is run your 12/3 from 2 20A Single pole Breakers. Inside the electrical panel all the neutrals are connected together regardless. So Sharing a Neutral is not an issue (Typically the Blue wire - taped white on both ends) then RED and Black on each of the single pole 20A Breakers. No issues as long as your cable is secured and out of harms way.
Page created in 0.148 seconds with 33 queries.